Some older fluorescent fixtures and those under 20 watts often require starters, which are the small aluminum or plastic cans in a socket near one end of the lamp.
If a new lamp is operated with an old starter the new lamp will exhibit premature blackening at its ends due to sputtering of the emitter on the lamp electrodes. This leads to accelerated aging of the lamp and therefore to premature failure. For this reason the starter must always be replaced together with the old fluorescent lamp.
Guide to Starters.
Osram. [No date] Page 6.
When its starter fails the lamp won't ignite, but starters are easily replaceable.
Twisting a starter less than a quarter turn counter-clockwise frees it from its socket.
Starter types are numbered, with the prefix FS (fluorescent starter). The designation is printed on the can or stamped on its end. The type must match the wattage of the lamp.
|Starter||For use with|
|FS-2||F14, F15, F20 preheat fluorescent lamps|
|FS-4||F13, F30, F40 preheat fluorescent lamps|
|FS-5||F4, F6, F8 preheat fluorescent lamps|
|FS-12||FC12 Circline lamps when operated by preheat ballasts;
F22 T8 preheat lamps; F32
|FS-20||F15, F20 preheat fluorescent lamps|
|FS-25||FC6(20W) and FC8(22W) Circline lamps when operated by preheat ballasts;
F25 and F18 T8 preheat lamps.
|FS-40/400||F40 preheat fluorescent lamps|
Most new fluorescent fixtures are either rapid-start or instant-start types that do not require starters. Some low-wattage desk fixtures and fluorescent lanterns require a person to be the starter by holding down a push button until the lamp ignites. The increasing use of electronic ballasts is making starters obsolete.
Return to main page on fluorescents
Sorry. No information on contributors is available for this page.
Copyright © 2008 Sizes, Inc. All rights reserved.
Last revised: 1 January 2008.